In the Guelph area, Aido Climate Solutions Inc. is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Aido Climate Solutions Inc. because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace and Air Conditioning Repair in Oakville, ON. Call us today at (519) 835-2436!
Summertime Air Duct Repair Service near Wolsey Crescent.
Summertime HVAC Maintenance near Falgarwood. Visited a repeat client's home to check the HVAC system for any components that could be affecting performance. Full-service diagnostic maintenance was performed. The filters were changed, and the condensate drain was cleaned. The system successfully maintains a comfortable temperature within the house.
Summertime Air Duct Cleaning Service near Glen Abbey. Came to perform annual ductwork cleaning for a residential client. Came out and cleaned the ductwork, which decreased the chances of upcoming HVAC system maintenance.
Summertime Air Duct Cleaning Near Falgarwood. Visited a return residential client for their annual ductwork cleaning. We cleaned the ductwork throughout the entire house, decreasing dust in the home, and reducing the need for repairs to the HVAC system.
Summertime Ductwork Repair Near Uptown Core. Got called to a residential home for a broken air duct. The issue was causing high utility costs for the homeowner. Arrived and replaced the broken air duct to repair the problem and lower utility costs for the happy customer.
Summertime A/C maintenance for a residential customer near Sunningdale. Cleared drain line Delta T is good. Condenser visually looks good Capacitor has a low reading replaced 45/5 if capacitor Pressure, tempature and charge are all good Units in good working order at this time
Cleaned furnace drain trap Adjusted slope on furnace drain Adjusted slope on furnace vent Camera inspection of primary and secondary heat exchangers Performed Flu analysis to ensure furnace working properly
Generalaire Model 3200DMM Bypass Humidifier w/ Water Savor Module
Maintenance: Thermostat working Checked gas pressure: 1.9" w.c. low 3.46" w.c. high Cleaned flame sensor Checked operations of safeties Checked furnace filter Checked operation of humidifier Performed flue analysis: furnace operating efficiently
Estimate on water heater , AC and Furnace.